View more items from this manufacturer
USED. Dismantled and ready to ship
|Loading Costs:||1100 Ton per unit (2200 Ton total).|
|# of Bids:||2 PLACE A BID|
|Product Location:||United Arab Emirates|
|End Time:||Bid As Soon As Possible|
|Time Remaining:||Bid As Soon As Possible|
|Trader:||Mohamed Ahmed +1 (832) 699-0014ASK A QUESTION|
This lot of Frame-9 ALSTOM Gas Turbines (2 Units) is no longer needed for the company's own operation & is being sold to recover funds. Details are listed below:
GT No: 8: Installed in the year 2000, was operational until end of 2007. Then the unit shut down normal and kept standby. Later, few spare parts had removed from this unit including cooling water radiator to install in FEWA GT units in another site. Currently, all removed parts including radiator assembly have been returned and installed in place.
GT No: 9: Installed in the year 2003, was operational until end of 2008. The unit shut down normal and kept standby.
In the year of 2008 onwards FEWA did dot require power generation from these GT units, FEWA decided to hand over to ADWEA. Since then both GT units remained idle in the existing location. No preservation was done for the plants for long term shut down. Subsequently, FEWA withdrew all the staff from the station, station supply disconnected, liquid fuel connections removed and Emarat disconnected the gas supply and removed gas fuel ESD valve.
Since the units were idle for almost 8 years, FEWA intend to rehabilitee these units to put back in service by floating this enquiry, before handing over to ADWEA.
Operational and Maintenance History of the Units:
The operational data is given below:
|Unit GT: 8||Unit GT: 9|
|1||GE Gas Turbine||TURCO-T9E148|
|2||Model||PG 9171 E|
|5||Last Run Date||29/1/08||26/5/08|
|6||Total Fired Hours||21669.4||13665.9|
|7||Gas Fired Hours||541.9||1544.4|
|8||Distillate Fired Hours||21148.9||12777.7|
|9||Manually Initiated Starts||275||143|
|12||Peak Load Fired Hours||2.6|
During the above operational period, two combustion inspections had been carried out an interval of 7000 operating hours and one hot gas path inspection carried out at 21660 hours. During HGPI, all the crossfire tubes, combustion liners, transition pieces, first and second stage nozzles, and first stage buckets were replaced.
During the above operational period, one combustion inspection had been carried out an interval of 7000 operating hours. Both units did not face any abnormal operational issues or breakdown maintenance.
|Generator||Unit GT: 8||Unit GT: 9|
|3||GT Type||Frame. 9||Frame. 9|
|4||Generator Type||T 240-370||T 240-370|
|5||Rating||122 MVA||165 MVA|
|8||Frequency||50 Hz||50 Hz|
To place bids or to sell items on this site, you must first become a member.