View more items from this manufacturer
|Product Location:||Arizona, United States|
This Hitachi Transformer is being sold to recover funds for the insurance company after the unit suffered damage during synchronization.
Hitachi Preliminary Investigation: Identified the unsynchronized energization (including severe surge voltage) was the main cause of the accident. Sequence of events can be reviewed in attached document. *** For full report and inquiries please email me email@example.com
Notes per Claimant: The two outside phases were severely damaged and all three HVB’s were also severely damaged. The tank is deformed and there were some small leaks. There was no fire. The new identical transformer will cost $1.7M delivered. Some minor disassembly has been done – low voltage bushings disconnected, oil removed, inspection hatches opened.